An Introduction to Condensing Boilers
(also known as Condensing Water Heaters)
Australia lags the world in the adoption of condensing boilers, so the opportunities for this technology in new and retrofits situations are many and highly beneficial. This series of articles will explore condensing boiler technologies and their applications and benefits. In Europe, condensing boilers have been proven for many years and their usage has become mandatory in order to comply with regulations and emission restrictions.
This is the first of a series of articles contributed by Dr Paul Bannister, a thought leader and public speaker on energy and energy efficiency issues in Australia. For other articles in this series, please refer to the links at the end of this article.
What is a Condensing boiler?
A condensing boiler; also known as a condensing hot water heater although referred to as a boiler in this article, is a type of boiler that is much more efficient than the traditional type appliance. Extra efficiency is achieved by extracting more heat out of the flue gas as compared to that of a conventional boiler. To understand how this process works, we have to consider some basic chemistry.
When gas burns, it combines with oxygen to produce carbon dioxide and water and some other by-products. For instance, methane gas (natural gas).
Where ΔE is the energy released in combustion. The size of ΔE depends on the final state of the carbon dioxide and water. The cooler they are, the more spare energy there is. For the water, this is particularly important because if the water is vapour, then it carries a lot more energy than if it is liquid. So if, on leaving a boiler, the flue gases are cool and the water is liquid, then the amount of energy ΔE that we can use is going to be larger. In a condensing boiler, the water is condensed inside the boiler so more energy can be extracted; in a conventional boiler, the water escapes as vapour and the energy is lost.
To be able to condense the water vapour from the flue gas, the condensing boiler should operate using a lower entering water temperature than a conventional boiler. This is because the condensing process occurs at around 54°C. You can still run a condensing boiler at a conventional 60°C return temperature, but the efficiency benefit won’t be as good as if it runs in condensing mode.
A conventional boiler will typically have a minimum entering water temperature of around 60°C, with an exit temperature of 80°C, and will not have the heat exchange elements in place to achieve the extra heat recovery in any case. Indeed, if condensing does occur in a conventional boiler it’s a bad thing – because the condensate does include acidic by products that will corrode the inside of the boiler and ultimately cause it to fail. Condensing boilers have additional heat exchange elements and are manufactured of the right materials to withstand corrosive condensates.
How efficient is a condensing boiler?
The efficiency of a boiler is measured by the ratio of energy output to energy input. To complicate matters, there are two conventions for measuring the energy content of gas:
- Gross calorific value: this is the energy released in combustion assuming that the water in the flue is liquid
- Net calorific value: this is the energy released in combustion assuming that the water in the flue is vapour.
The correct figure to use when considering a condensing appliance is always the gross calorific value, which is the larger value. However, some promotional literature for conventional boilers will use the net calorific value, because this makes their conventional boiler look more efficient.
Using Gross calorific values, conventional boilers are typically around 80-83% efficient at full load. By contrast, a condensing boiler using the same basis is around 95% efficient at full load. If the condensing boiler isn’t running in condensing mode it will still have a 4-5% better efficiency than a conventional boiler because of its superior heat exchange and burner control.
Using Net calorific values, these figures both increase by about 10%, so that the condensing boiler has an apparent efficiency of 103% – because it is extracting more heat from the flue gas that the net calorific value recognises.
So the immediate benefit of a condensing boiler is an improvement in efficiency of at least 10-15%. But it’s actually much better than that, as we will explore in later articles.
Articles in this Series
An Introduction to Condensing Boilers
- What is a Condensing boiler?
- How efficient is a condensing boiler?
- Efficiency at part load
- Benefits of reduced operating temperatures
- Heating Load Profile
- Efficiency Benefits
For more information about Condensing Boilers, please refer to our Condensing Boilers Explained page